Iso 6 cleanroom supplier 2022? In order to maintain the required temperature, humidity, wind speed, pressure and cleanliness in the clean room, the most commonly used method is to continuously send a certain amount of treated air into the room to eliminate various heat and humidity interference and dust pollution in the clean room. To obtain the air in a certain state into the clean room, a whole set of equipment is needed to process the air, and it is continuously sent into the room, and part of it is continuously discharged from the room. This whole set of equipment constitutes a clean air conditioning system. Discover even more information at iso7 cleanroom.
Clean air-conditioning system is to control outdoor substances that affect the clean environment of clean rooms, such as dust, smoke, microorganisms, etc. It is a very important part in medical and health, food processing, and microelectronics engineering.
The clean air conditioning system is basically composed of the following equipment:
1. Heating or cooling, humidification or dehumidification and purification equipment;
2. Air conveying equipment and pipelines that send the treated air into each clean room and circulate it;
3. Provide heat, cold, heat source, cold source and piping system to the system.
This specification is formulated to set important national guidelines and rules, unify construction acceptance requirements, unify testing strategies, and ensure project top quality, save more energy, protect the environment and safe operation during the construction of clean rooms (including prefabricated clean rooms, the same below). This specification is applicable to the construction and acceptance of newly-built and reconstructed industrial clean rooms and general biological clean rooms, and is not applicable to the construction and acceptance of special biological clean rooms with biological safety requirements.
The clean room workshop is also called the dust free workshop, gmp cleanroom, the industrial clean room (Clean Room) and the dust free room. It refers to the removal of pollutants such as particles, harmful air and bacteria in the air within a certain space, and the indoor temperature,cleanliness, indoor pressure, air velocity and air distribution, noise and vibration, lighting and static control. A specially designed clean room for a particular requirement. That is to say, no matter how the extemal air conditions change, the clean room can maintain the characteristics of cleanliness temperature and humidity and pressure.
In Africa, some area only require cooling system of the air conditioning unit. Especially at island country, the air humidity is very higher 80-90% of year average. For noodles, pasta production factory, the humidity should be control at 30-40%. Like this condition we recommend rotary dehumidifier air conditioner or independent dehumidifier with air conditioner work together.
For the unidirectional flow (laminar flow) clean room, the air supply volume is determined by the product of the average wind speed of the room section and the cross-sectional area, in which the measured section of the vertical unidirectional flow (laminar flow) clean room is the horizontal section 0.8m away from the ground; The horizontal unidirectional flow (laminar flow) clean room takes a vertical section 0.5m away from the air supply surface. The spacing of measuring points on the section shall not be greater than 2m, and the number of measuring points shall not be less than 10, which shall be evenly arranged. Hot bulb anemometer for instrument.
Today (Suzhou Pharma Machinery Co., Ltd.) will introduce to you, clean room airflow and influencing factors. There are many factors affecting the airflow in the clean room, such as process equipment, personnel, clean room assembly materials, lighting fixtures, etc. At the same time, the distribution point of airflow above the production equipment should also be considered.
Suzhou Pharma engaged in cleanroom turnkey project for many years, HVAC system design and installation is the main part in project. We supply air duct design, AHU solution and installation guide. Before we quote the equipment, the basic data is necessary, such as room clean grade, dimension and height, temperature and humidity request, the local highest/lowest temperature and humidity.
A clean room refers to the removal of particulates, harmful air, bacteria and other pollutants in the air within a certain space, and the indoor temperature, cleanliness, indoor pressure, airflow speed and airflow distribution, noise vibration and lighting, Static control is within a certain demand range, and a specially designed room is given. That is to say, no matter how the external air conditions change, the interior can maintain the characteristics of cleanliness, temperature, humidity and pressure that were originally set. The main function of the clean room is to control the cleanliness and temperature and humidity of the atmosphere that the product comes into contact with, so that the product can be produced and manufactured in a good environmental space. We call such a space a clean room.
What is the purpose of the clean room test of the clean workshop? Most of the owners are based on the original vision of the purification project to complete the test indicators. Of course, this is the most straightforward goal and method. After all, our intention to build a clean room is also As such, there is a need to achieve our air cleanliness. In a single-flow type clean room, the location of the wind speed measurement can be specified by the owner, usually on the surface of the filter screen or at the working height. However, it should be noted that it is the air velocity measurement of the filter screen (the surface of the filter screen) or the indoor air velocity measurement of the clean room (working height). Clean workshop, clean room, clean room — the purpose of clean workshop and clean room test. Find extra info at https://www.sz-pharma.com/.
Governments of various countries have different requirements for clean design conditions, so attention should be paid to government requirements when designing. The choice of refrigerant should pay attention to whether it needs environmental protection type.
The cleanroom advantage include:
1. handmade sandwich panels can always be customized to meet every need,module width, module height are variable dimensions. no need cutout in the Installation site.
2. GMP double layer glass walls can customized.They allow to see into the production process and create a different working atmosphere.
3. LED lights reach UL standard.
4. For special hygiene requirements, our offers higher-quality integrated,hollow-profiles systems that prevent ingress of dire,air dust and moisture. Our design according to ISO14644-1 International standard.
Suzhou Pharma hope that in this new year, we have a new breakthrough in clean room technology, which can help more friends in need.